NO Water? No Water Pressure? Out of Water?
There is nothing more annoying than going to wash your hands at the sink at your Dodge County house and find out that there is no water at all! No water pressure - what do you do?
Homeowners in Dodge County contact the plumbers at Austin Plumbing Company for immediate help. No water means you are having a problem with your submersible well pump. Or, the problem could be with the pressure tank.
Well Pump With No Pressure
There are a couple of quick reasons you may find yourself with no water pressure in your Dodge County house. The circuit breaker could be tripped causing no electricity to the well pump. There is also a possibility the pressure switch could be failed. Turn the circuit breaker on and off, back to on and see if your well pump kicks back on. View the contacts on the pressure switch. The contacts on the pressure switch should be clean and free of debris build up. Be careful there is 115 volts or 220 volts of electrical power supplying the pressure switch control. It is most safe to turn off all power when working on the well system even if you’re observing from a close distance. Always turn off the power to the pressure switch before removing the cover.
Do you know where your well is located in your yard in Dodge County? With the power off remove the well cap. Observe all electrical wires look for arching or any wire that may be burnt or shorted out. If you find a burnt or shorted out wire this will cause a no water situation. If all electrical connections appear to be in good order turn the power back on and listen for the sound of your submersible well pump running. If you hear the pump running for a few seconds than turn off and back on again your well pump motor may be damaged. If you are capable, disconnect the wires at the well location and check for proper electrical current.
If you are still experiencing no water, very poor water pressure, or water that is fluctuating up and down contact Austin Plumbing Company or give us a call at 262-367-3808. Smell Good Plumber help will be on the way to your Dodge County home.
Submersible Well Pump
Did you ever turn on a faucet to find no water pressure at all? If your well pump keeps losing pressure, or you continue to run out of water you could have one or more of these common water pump problems in your Dodge County home. Before assuming that there is no water at all in the well, check to see that your water pump is functioning properly. See if the check valve or foot valve could be causing the problem. In some cases, a hole in the pipe leading to the pump can occur. This happens most frequently between the pressure vessel and the submersible water pump. And of course there is a chance that the pump system has just quit pumping water.
Unfortunately, when a water pump decides to quit working often times there are no advanced warning. Did you know that the average life of a submersible well pump is 10 years? However, we have replaced many well pumps that have been in operation over twenty years. Residence of Dodge County have found the life expectancy of a well pump can vary depending upon the quality of the water in the well. When areas have high iron and sulfur content, water pumps do not last as long.
There are several major brands of submersible well. A few common brands include Goulds Pump, Webtrol Pump and Myers Pump. This list is not a complete list but is a good sampling of the major brands found in the Dodge County area we serve. Most well pumps manufactured today have a Franklin Electric motor. If you are experiencing any water pump issues or low water flow issues please contact Austin Plumbing Company or call your Smell Good Plumber at 262-367-3808.